Steel pipes are the most commonly used pipes in water supply systems. They are also used in pipelines for natural gas, and sewerage systems. Although comparatively expensive to other pipes, they hold the advantage of being able to withstand high pressures and are available in more convenient lengths, and can also be welded easily, thereby resulting in lower installation and transportation costs. These types of pipes are highly efficient and can be used in small diameters as needed and are 100% recyclable compared to other materials. The pipes can further be melted down and turned into other usable material in industry. Furthermore, the high strength of these pipes and resistance to damage caused by human errors, tree roots, and extreme weather conditions make these pipes the ideal choice for most water and sewerage supply systems.
The disadvantages of steel pipes include thermal conductivity, which is very poor as there is a difference in heat transfer. These types of pipes are usually bonded with aluminum or copper alloy to increase thermal conductivity and improve heat transfer. Cost is another issue, as these pipes are expensive and this is guided by the misconception of being a one-time purchase. However, steel pipes are difficult to fabricate and lack the malleable qualities that other materials have, therefore repairs and replacements of steel pipes are extra difficult.
Basic material properties
Steel is strong, rigid, and has a low coefficient of thermal expansion. It is also heavy (multiple workers may be needed to transport it) and is subject to corrosion. Sometimes it is called carbon steel or black special steel to differentiate from stainless and galvanized steel. All steel, by definition, contains carbon.
Steel often is used for closed hydronic systems because it is inexpensive, especially when compared with other materials in systems with high pressures, and corrosion is relatively easily controlled in these systems. It also is a good choice for steam and steam-condensate systems because it handles high temperatures and pressures well, and corrosion is normally not an issue in steam pipes. However, corrosion is an issue in steam-condensate pipes, and many engineers specify schedule 80 steel pipe simply because it takes about twice as long to rust through as schedule 40 pipe.
If amines (commonly cyclohexylamine, morpholine, or diethylethanolamine (DEAE) are fed properly to neutralize condensate pipe pH, condensate pipes can last the life of the building. Some building owners do not want these chemicals in steam that may be used for humidification because of health concerns; however, not using these amines might require a change to stainless steel (SS) piping or adding a separate “clean steam” system for humidification and for sterilization of medical instruments.
Rigidity is important because it determines the distance between hangers. Steel pipe is manufactured in 21-ft lengths, and the hangers can be spaced that widely for large-diameter pipe. More flexible materials, however, may require hangers on as close as 4-ft centers or even continuously. Consult ANSI/MSS SP-58: Pipe Hangers and Supports – Materials, Design, Manufacture, Selection, Application, and Installation for details about hangers and hanger spacing.
A low coefficient of thermal expansion minimizes the need for expansion loops and expansion joints. However, the high rigidity of steel means that although it expands less, it exerts very high forces on anchors.
Galvanized steel pipe is steel pipe that is dipped into a pool of zinc (see Figure 1). Galvanizing has two methods of corrosion reduction:
It coats the surface like paint, and under most circumstances it forms a very adherent oxide layer like aluminum and SS.
It provides a sacrificial anode (zinc) to receive corrosion instead of the steel corroding.
Galvanized steel pipe has all the advantages of steel pipe, and is used in insulated and coated piping, plus improved corrosion resistance in most environments, although at a slightly higher cost. Galvanizing works almost perfectly in applications where it is wetted and dried periodically (e.g., road signs and guard rails). It can fail in environments with high sodium (e.g., softened water that started out very hard) because the sodium makes the adherent oxide film detach and react more like steel pipe where the oxide flakes off. If galvanized pipe is being welded, the welder needs to be careful to grind down to the raw steel. Repairing galvanizing on the inside of the pipe is difficult or impossible. If the interior needs a continuous galvanized layer, consider mechanical couplings. (More information is available via the American Galvanizers Association.)
Copper pipe often is used in both hydronic and domestic applications, especially for 2-in. and smaller pipe sizes. However, some contractors propose replacing galvanized steel domestic-water pipe with copper up to 6-in. in size, especially in the Midwest. Copper is an expensive material but has the advantage of weighing less than steel and may require fewer employees to install, depending on weight and union restrictions. Also, copper is generally more noble and corrosion-resistant than steel or galvanized steel pipe fittings.